General conditions for installationConnection IN & OUT:
3/4", 1" or 1.25" dependent on flowElectrical rating:
230V 50Hz 12V TransformerMax power rating:
6WIP protection class:
Double isolated transformerMinimum inlet pressure:
200 kPa (2 bar)Maximum inlet pressure:
600 kPa (6 bar)Vacuum:
no allowanceAverage pressure loss (**):
100 kPa (1 bar)Min-max water temperature:
(*) Dependant on Drain line flow control.
(**) Under normal circumstances.
It is always recommended to install a 25 micron cartridge filter before a softener.ResinType:
Strong acid cation resin - softening ,food grade qualityLife span:
15 years under normal circumstancesIon exchange ( for average salt consumption of 150 g/L )RegenerationStart:
Default Time 2:00 am, set on the timer as ( delayed regeneration )Options:
TIME - VOLUME - IMMEDIATE - DELAYED - DAYS OVERRIDE and manual regeneration.
The interval between regenerations should not be more than 14 days, to prevent bacteria growth.Flow RateConsumption of Rinse Water